Remove the detector from the Loop.
Connect the detector to the handheld programmer, Easy Check. This is done either via the integrated detector base or the connecting cable and read out the detector address (stored in the detector) .
Check the software compatibility list, if the new detector is compatible with the Loop module of the fire panel.
Take the new detector and connect it to the handheld programmer, Easy Check. This is done either via the integrated detector base or the connecting cable and assign the same detector detector address as that one to be replaced.
If the detector type of the old detector and the new detector are identical, no further steps are necessar, apart from a functional test.
In all other cases, a new strt the menu item, detector scanning is required. Pay attention to the correct input of the Loop module address.
While doing disablements of detectors or of zone disablement of OMS module please regard the system parameters 20.2 in the dpt.
Default setting is that you can only activate the collective diablement 'external sounders off.
If you want to enable a zone or even a detector disablement of OMS modules, please set the system paramter 20.2 to the value 'only disablement of zones of sounderss possible 'or' shutdown of individual devices.
From the 6E_05_XX onwards the input 3 of the motherboard is used as a fault input on the network. This makes it possible to evaluate a fault of the optical fiber converter or the 2-wire repeater. If none of these devices will be in operation, it is necessary to bridge this input with 0 V.
Check the parameter 16 of the system menu.This parameter should be 01 for a 3004 panel and 02 for a 3004plus panel. Also please check your null modem cable for a proper wiring; optionally for a defect.
Since the 3004 only has an RS 232 interface, it is necessary to operate the protocol printer via a special firmware of the company IFAM over the FAT 2002/3000. In this case, the RS 232 interface of the FAT is used and connected to the log printer in the office. If the distance is more than 15 meters, an RS 232 / RS 485 coupler is required. For more information and documentation, please contact our hotline.
If you would like to participate in one of our company's services, be informed individually by e-mail or by post, the processing of personal data is necessary. In this context, all companies are required by law to obtain the consent of the person concerned
We would be pleased to inform you free of charge about: